Buy ASTM D SPECIFICATION FOR GLASS-FIBER-REINFORCED POLYESTER UNDERGROUND PETROLEUM STORAGE TANKS from SAI. ASTM D Standard Specification for Glass-Fiber-Reinforced Polyester Underground Petroleum Storage Tanks CONTAINED IN VOL: – Find the most up-to-date version of ASTM D at Engineering
|Published (Last):||14 March 2015|
|PDF File Size:||16.13 Mb|
|ePub File Size:||1.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
The installation has been inspected and certified by a registered professional engineer with education and experience in UST system installation. For a volume license the PDF is licensed to the person in which it is assigned.
Refer to Sections 23 03 00, 23 20 00 and 23 20 10 for additional requirements.
MIL-T A TANKS STORAGE UNDERGROUND GLASS FIBER
Distribution of the PDF is not permitted. Handle fuel oil system components carefully to avoid damage to material component, enclosure and finish. Reference the current page of this Report. Repeat inspection and tests. Provide a complete fuel oil supply system including pumps, piping, fittings, valves, controls and accessories as specified and required for a complete and operating system.
Following is a list of organizations and the titles of a few of their standards or codes that relate to UST management: Compression molded using epoxy molding compound and bearing the same UL label as pipe for fiberglass and as specified for piping above grade for steel. Stockham Valve and Fittings. Provide products complying with these specifications and produced by one of the following: Valves shall be designed to reduce psi to 20 psi in the fuel oil return line and shall be rated for psi WOG.
Install fiberglass piping systems in accordance with the manufacturer’s written installation constructions. Provide an electronic monitoring system to monitor the fuel oil level in the fuel oil storage tank, monitor the tank for leakage and detect the presence and amount of water in the tank with the fuel. View a full description of this report. Pumps, casings, connections, and mechanical seals shall be rated for operation at the system working pressure.
Valves used for balancing shall be provided with balancing stops. Provide H 20 rated steel traffic cover manholes, minimum 14″ diameter, with sump for installation of monitoring probes. Specification c Amendment 1 February Page 3. Search Inside This report can be searched.
Pumps shall deliver the capacities scheduled or shown on the Drawings. Sleeve piping penetrations through concrete construction. Refer to Section 23 03 00 for applicable painting, nameplates and labeling requirements. Provide a double wall, secondary containment system over all primary fuel oil piping, d40221 of an outer 0.
State environmental compliance is probably your biggest job challenge—the regulations and laws are so complex and they change so fast! Submit complete wiring diagrams for pump controllers and monitoring equipment. Pumps shall be UL listed and labeled for installation and operation in a Class 1, Division 1, Group D hazardous location.
Use John Crane, or approved equal, or teflon thread tape applied only to male threads to make up joints. Pipe shall bear UL label for petroleum products’ piping. Ball valves shall be two piece, full line size full port stainless steel balls and stems and reinforced seats and stuffing box rings. Valves shall volt rated coils with Class F insulation and shall be of a normally closed fail closed design.
Sump bottom shall have openings for entry of piping riser with secondary containment and conduit. Use on a local area network or other network is not permitted.
More About Petroleum USTs
Provide adapters as required for connections to threaded piping. Refer to Section 23 20 00 for requirements. Certify that the complete fuel oil and monitoring systems are installed in accordance with all applicable local, axtm and federal codes, standards and regulations. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Citing and Sharing Basic information for referencing this web page.
Technical standards | All-Standards
All connectors shall be suitable for use at the pressure and temperature encountered at point of operation. Check valves 2″ and smaller shall be Class threaded bronze swing check valves with horizontal swing and replaceable discs.
Refer to Section 23 03 00 for additional requirements. Provide the services of a factory service engineer to checkout, start up, calibrate and certify monitoring systems.
SECTION 22 50 00 FUEL OIL PIPING SYSTEM PART 1 – GENERAL
NR Fuel Tender Inspection. UST owners must fill out a notification form certifying that the tank and piping were installed according to industry codes. This standard does not purport to address all of the r4021 problems, if any, associated with its use. Install pumps where shown, in accordance with manufacturer’s written instructions, and recognized industry practices, to ensure that pumps comply with requirements and serve intended purposes.