Nominal dimensions and physical characteristics for copper tubes type K and L according ASTM B Standard Specification for Seamless Copper Tube for. Copper Tube Medical Gas ASTM B Type K Specification including outside diameter, wall thickness and weight. Find the most up-to-date version of ASTM B at Engineering
|Published (Last):||3 October 2009|
|PDF File Size:||16.99 Mb|
|ePub File Size:||14.51 Mb|
|Price:||Free* [*Free Regsitration Required]|
Mechanical Properties The tube shall conform to the mechanical property requirements specified in Table 2 when tested in accordance with Test Methods E 18 and E 8, respectively. A convenient method of indicating that these tests are to be made is to state that “Test Procedure T” is required see 4.
Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard. This specification establishes the requirements for two wall thickness schedules of specially cleaned, straight lengths of zstm copper tube, identified as Types K and L, suitable for medical gas systems.
ASTM does not give any warranty express or implied or make any representation that the contents of this abstract b8819 accurate, complete or up to date. Other information maybe included atthe 0ption ofthe manufacturer. The deviation from roundness is”measured as the difierence between major and minor axtm as determined at any one cross section of the tube, N819 r The manufacturer of supplier shall inspect and make tests necessary to verify the product furnished conforms to the requierements of thus spseciflcation.
The tube shall conform to the mechanical property requirements specified in Table 2 when tested in accordance with Test Methods E 18 and E 8, respectively.
DENJI ASTM B819
Where agreement on the Rockwell hardness tests cann0t be reached, the tensile strength requirements of Table 2 shall be the basis for acceptance or rejection. Material-The materials of manufacture shall be a cast billet of Copper Alloy UNS Cl of such purity and soundness as to be suitable for processing into the products prescribed herein.
The values stated in inch-kpound units are to be regarded as standard, The values given in parentheses are mathematical conversions to Sl units,which are provided for information only and are not considered standard. The cleaner may contain but is not restricted to tri ortetra sodium phosphate, sodiurn carbonate, sodium hydroxide, sodium metasilicate, or sodium orthosilicate plus a wetting agent or any combination of the lore going.
Product: Copper Tube ASTM B819 Type K Specification
Rejection should be reported to the producer or supplier promptly and in writing. Note 2-Drawn tempertube is suitable for use with capillary solder joint fittings for brazing. The following are recommended practices lor cleaning, butthe produceris nota limited to these procedures.
Historical Version s – view previous versions of standard. B89 tests and the inspection shall be conducted so as not to interfere unnecessarily with the operation of the works.
Tension test results on material covered by this specification are not seriousle affected by variations in speed of testing. Package Marklng-Each shipping unit shall be legibly marked with the purchase order number, metal or alloy designaiion, size, gross and net weight, and name of supplier. Tension test determinations need not be made except when indicated by the purchaser at satm time of placing the order.
ASTM B – 18 Standard Specification for Seamless Copper Tube for Medical Gas Systems
The value for the Rockwell hardness number of each specimen shall be established by taking the arithmetical average of at leastthree readings. When specified in the contract or purchaser order the purchaser shall be furnished certification that samples representing each lot have been tested or inspected as directed in this specification and requirements have been met.
Number of Tests and Retests Chemical Analysis-Atleast two replicate analyses of each element with a limiting value shall beconducted. Seamless copper tube for medical gas systems shall be furnished in the H58 Drawn General Purpose temper. Dimensions, Mass and Permissible Variations For the purp0se of determining conformance with the dimensional requirements specified in this specification, any measured value 0utside the specif ied limiting values for any dimensions may be cause for rejection.
After washing and drying, the tube shall be immediately capped, plugged, 0r otherwise scaled 0r closed at both ends. The manufacturer or supplier and the purchaser may conduct the final inspeciton simultaneously by mutual agreement.
Theoretical wights for purposes of caculating weights, cross sections, and so forth, the density of the copper shall be taken as 0. When specified in the purchase order or contract. Test specimens conforming to type No. Above the yield strength, the movement per minute of the testing machine head undgr load should not exceed 0. Product that fails to conform to the requirements of this specification may be rejected.
ASTM B – 00 Standard Specification for Seamless Copper Tube for Medical Gas Systems
The legend shall include the type of tube, name or lrademark of the manufacturer or both, and the country of origin. Link to Active This link will always route to the current Active version of the standard. This abstract is a brief summary of the referenced standard. Drawn temper tube is suitable for use with capillary solder joint fittings for asfm.
The product shall be separated by size,composition,and temper and prepared for shipment in such a manner asmt to ensure acceptance by common carrier for transportation at the l0west rate applicable and to afiord protection from the normal hazards ol transportation. Certification When specified in the atm or purchaser order the purchaser shall be furnished certification that samples representing each lot have been tested or inspected as directed in this specification and requirements have been met.
Mechanlcal tests-For the mechanical tests,a specimen shall be taken from each of the sample pieces selected in accordance with The tubes used for medical gas systems shall be cleaned by satm of the following recommended methods: Rehearing – As a result of product reiection, the manufacturer or supplier may make claim for a retest to be ‘ conducted by aatm manufactuer or supplier b19 the purchaser.
Failur of more than on specimen to meet the specified requirements atm aparticular property shall be the cause for rejection of the entire lot. Whenever different tension test results are obtained from both full-size and from machined test specimens, the results obtained from full-size test specimens shall be used to determine conformance to the requirements of this specification.
The product shall be manufactured by such hot working necessary to convert the billet to a tubular shape and cold worked to the finished size.
Types K and L tube are defined in Specification B Eddy-current test, a nondestructive test, shall be performed as well. This spesification establishes the requirements for two wall thickness schedules of specially cleaned, straight lengths of seamless coppertube, identified as Types K and 1, suitable for medical gas systems.
This standard does not purport to address all of the safety concerns, if any, associated with its use. The manufacturer of supplier shall inspect and make tests necessary to verify the product furnished conforms to the requierements of thus spseciflcation.
Tension test specimens shall be of the full section of the tube and shall conform to the requirements of 6. It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use ast, application.
This standard does not purport to address all of the safety concerns, if any, associated with its use. The following safety hazard caveat pertains only to the test method portion of Section dl2 aetm this specification. It is the responsibility of the user of this standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.